Home > Access Control > Network Systems > Impro Systems
Catalogue No: GB-MDR901Brand: Impro
Click for delivery info
The Impro Multi-discipline Readers are compact and robust Passive Proximity Readers. New technology allows the Multi-discipline Readers to read both 125 kHz and 13.56 MHz frequency Tags. These Readers fit seamlessly into new or existing applications allowing you to upgrade Tag technology without replacing existing Tags.
The design of the Multi-discipline Reader allows you to use them with a variety of Terminals and Controllers, within third-party or Impro Access Control Systems. When used with the IXP220 Controller, IXP20 Controller or the Impro iTRT, these Readers use AES 128-bit Encryption with a Diffie Hellman key exchange thus ensuring secure communications on the Wiegand Bus.
You can use the Multi-discipline Readers in both indoor and protected outdoor environments.
The Multi-discipline Keypad Reader offers a 12-button Keypad allowing PIN-code entry. All models include a single tone, single volume Buzzer and a single tri-coloured Red, Green or Amber Status LED. You can control the functions of the Buzzer and Status LED to suit the needs of your application.
The IXP220 system has a choice of configurations to suit the varying communications needs and budgets of your clients.The system can be configured using an IXP220 (GB/IPS963) system controller with up to 15 IPS920i economical, intelligent 2 door controllers, giving you control for up to 32 doors.
Just add another GB/IPS963 and another 15 GB/IPS920i controllers for a further 32 doors and continue to a maximum of 256 doors. Alternatively, should you need to useTCP/IP for all communications, the system can be configured using just the IXP220 (GB/IPS963) system controllers up to a maximum of 128 doors.
It is possible to mix and match the different configurations to suit the needs of the site.The main controllers work perfectly offline and communicate with each other to give you full anti-passback and input/output control even when off line from the PC. It is possible to use star or chain wiring configurations.
The maximum cable distance from the first to last controller is 1km, from the door controllers to readers 150m.
Education, Council, NHS, Police and Emergency ServicesClick Here
© 2017 OLSP Limited.
Order Helpline 0800 880 6123email: @ click here